The URL in the browser address bar is volatile and may be broken at any time.
To obtain a link to this page, click the <<Share>> button top-right of the screen.
Note - if the navigation pane on the left of this window is not visible, click the 2-pane icon on the top bar
Fairly common questions are:
which side to star the CT?
which side to have the polarity?
are there any consequences or implications?
The answer, as always, depends on the application, and then to some extent on the capabilities and settings of the IEDs!
If the protection elements "50" or "51" elements (IEEE C37-2008 are purely non-directional, they only operate on the magnitude of current so at least in that respect, polarity and star are immaterial.
The two independent choices star side and polarity sides is only a question of standardisation in order to be consistent across the various locations simply to ensure there is no confusion for the technicians.
Directional Current, Distance and Power- based Applications
However, if the "50" or "51" elements (IEEE C37-2008) are now directional as "67" devices, or perhaps a distance function "21", reverse/over power function "32", or any other power related function including metering etc, the direction of power flow becomes significant.
If the IED allows changing of the polarity seen by the IED as part of its available settings, the direction can be set to suit the application as part of commissioning.
As most modern directional-based relays have polarity settings. then as with non-directional relays, the polarity of the CT is arguably just a matter for company convention.
If we consider directional overcurrent and earth fault relays connected to CTs in a Holmgren connection, there are eight possible combinations requiring consideration of the protection element forward/reverse setting.
This can be shown if we consider an earth fault "downstream" of the CT point and the direction of current flow in the relay earth fault element that will cause operation.
P2 towards source
P1 towards source
CT Star source side
CT Star source side
This is arguably a little more complicated in the "it depends" consideration
Merz-Price Circulating Current High Impedance Differential
A phone call is nearly always welcome depending on the time of night wherever I am in the world. Based in Adelaide UTC +9:30 hours e.g.
Noon UK = 2030 Adelaide
Noon UK = 2230 Adelaide
Office + 61 8 7127 6357 Mobile + 61 419 845 253
No Liability: Rod Hughes Consulting Pty Ltd accepts no direct nor consequential liability in any manner whatsoever to any party whosoever who may rely on or reference the information contained in these pages. Information contained in these pages is provided as general reference only without any specific relevance to any particular intended or actual reference to or use of this information. Any person or organisation making reference to or use of this information is at their sole responsibility under their own skill and judgement.