The URL in the browser address bar is volatile and may be broken at any time.
To obtain a link to this page, click the <<Share>> button top-right of the screen.
Note - if the navigation pane on the left of this window is not visible, click the 2-pane icon on the top bar
The IEEE / ANSI Device Numbers described in IEEE C37.2 (latest version 2022) have been a fundamental basis of describing functions in the electricity industry.
Of course the generic purpose of such "nomenclature/semantic" standards is to eliminate ambiguity and arbitrary definitions that are not necessarily understood in the same way by others.
However there are many in the industry who have not delved into a full understanding of the entire C37.2 Standard and so can fall into "common errors" simply because they have seen someone-else's proliferation of incorrect terms.
Another is the subject of this post for the use of Device 64 .. sometimes incorrectly referred to as 64R or 87N.
Ironically, C37.2 Annex C titled “Device 64—Ground detector relay applications” has NO examples of 64 and only deals with N and G suffix!
64 is clearly a “restricted” zone of protection, only operating for a fault within that physical zone (usually defined by the CT locations).
64R has no direct relevant meaning under Clause 3.5 .. and if R is intended to be “Restricted” is a tautology of the meaning of 64 anyway.
87N is an intriguing interpretation. Certainly 64 is a differential application so I can see the leaning towards the overall definition of 87. However the use of N is an anomaly to the descriptions in Annex C.
Annex C clearly shows that N refers to the sum of the three line currents. However in the case of the Restricted Earth Fault application on a star winding, it is the sum of the three line currents AND the “negative” value of neutral earth leg CT in order to get the Kirchhoff’s node summation of ΣOut – Σin should equal zero. For a delta winding, Restricted Earth Fault is indeed the sum of the three line currents. However it is to note that there is no primary “neutral” so an N suffix to any device number for the REF function on the delta side would be misleading.
The following diagram provides the use of N and G suffix vs 64 as applied to a delta-star transformer.
It can be seen that "N" is not necessarily a "neutral" .. it would be more accurate to say that it is a "Numeric" summation of the three line currents either as connection of the phase CT secondaries or as internal numerical summation of the relay individual phase CT inputs.
A phone call is nearly always welcome depending on the time of night wherever I am in the world. Based in Adelaide UTC +9:30 hours e.g.
Noon UK = 2030 Adelaide
Noon UK = 2230 Adelaide
Office + 61 8 7127 6357 Mobile + 61 419 845 253
No Liability: Rod Hughes Consulting Pty Ltd accepts no direct nor consequential liability in any manner whatsoever to any party whosoever who may rely on or reference the information contained in these pages. Information contained in these pages is provided as general reference only without any specific relevance to any particular intended or actual reference to or use of this information. Any person or organisation making reference to or use of this information is at their sole responsibility under their own skill and judgement.